Here you can find all about Haier HM-07C03 like manual and other informations. For example: review.
Haier HM-07C03 manual (user guide) is ready to download for free.
On the bottom of page users can write a review. If you own a Haier HM-07C03 please write about it to help other people. [ Report abuse or wrong photo | Share your Haier HM-07C03 photo ]
User reviews and opinions
No opinions have been provided. Be the first and add a new opinion/review.
HM-07C03 HM-07C03/R1 HM-09CA03 HSM-08C03
Mobile type air conditioner
1.PRODUCT CODE ILLUMINATION AND SERIES INTRODUCTION.. 1 2. 2
3.PRODUCT SPECIFICATION.. 3 4.MAIN COMPONENTS AND ACCESSORIES NAME, DIMENTION AND FUNTION.. 5.
5 6.WIRING DIAGRAM.. 6 7. 7 8.SYSTEM FLOW CHART.. 8 9.INSTALLATION AND REPAIRING.. 9 10.SYSTEM FLOW CHART.. 10 11.INSTALLATION AND REPAIRING.. 11
High efficiency for saving energy Easy to move Low noise
PRODUCT CODE ILLUMINATION AND SERIES INTRODUCTION PRRODUCT TECHNICAL PARAMETER PRODUCT SPECIFICATION MAIN COMPONENTS AND ACCESSORIES'NAME, DIMENTION AND FUNTION 3
Mobile Type Conditioner Technical Manual
KNOCK-DOWN DRAWING AND LIST OF COMPONENT MICROCOMPUTER CONTROLING THE FUNCTION OF ELECTRIC CONTROL INTRODUCTION WIRING DIAGRAM MAINTENANCE ANDTROUBLE SHOOTING SYSTEM FLOW CHART
HM 07C03 HM 07C03/R1 HM 09CA03 HSM 08C03
11 INSTALLATION AND REPAIRING
1.RODUCT CODE ILLUMINATION AND SERIES INTRODUCTION a model code rule description
Standard situation/conditions No. Operating condition D. B. 1 Nominal cooling Nominal heating Nominal electrical heating 30 / / Indoor air state W. B. 26 / / D. B. 30 / / outdoor air state W. B. 26 / /
H S M A BC
A:Abbreviation of Haier B:Abbreviation of Split C:Abbreviation of Mobile D:Nominal cooling capacity(BTU/h)with the fitst two numbers based on one thousand unit E:Function code C-Cooling only H-Heating pump E-Electric aided heating F:Developing sequence G:The type of power supply H:The kind of refrigerant Examples: Hsm-08C03 -It represents Split-Mobile air conditioner.Cooling capacity is 8000 BTUh and the power supply is 200~230V/50Hz.
Brief introduction of mobile window air conditioner series
The product of mobile air conditioner is the now type of air conditioner developed by our company, its main character is:there aie four foot wheels in the botton of indoor unit, which can move among each apartment of the room. For whole mobileair conditioner suchas HM-07C03, HM-07C03/R1, HM-09CA03, hat between indoor unit and outedoor unit can be exchanged through wind pipe, for split-mobile air conditioner such ad HSM-08C03, heat can be exchanged through outdoor unit. Drainage of mobile air conditioner use the principle of gravity drainage, having the cooled water flown into water tank,pour it out when the tank is full. This type of product have the advantage of easy installation without breaking the wall, so it is very popular with many consumers.
PRODUCT SPECIFICATIONS The manufactur reserves the right to change any change any product specifications without notice. Item Cooling capacity Heating capacity Power supply Power factor Cooling Power input Running current EER Power input Running current COP Indoor side Outdoor side Height Width Depth Height Width Dpth Net Gross Type Model Heating side Cooling side Model charge Type Fan Fan speed indoor unit outdoor unit Hi Lo UNIT BTU/h BTU/h % W A BTU(hW) W A BTU(hW) dB(A) dB(A) mm mm mm mm mm mm kg kg HAM-08C03 HM-09CA900 / / 1PH,220~50Hz 1PH,220~50Hz 0.96 0.1100 4.6 5.3 8.6 8.2 / / / / / / / / TOSHIBA TOSHIBA PH150X1C-4DZ2(2000165) PH165X1C-4DZ2(2000165) 2.65 2.65 2.65 2.65 R22 R22 0.75 0.6 inertialfan inertialfan Axial fan / 60~70 60~260 -3 1.1.6 10-3 CE CE evaporator: 7condenser: 9 evaporator: 7condenser: 9 / / Hydrophile aluminum foil Hydrophile aluminum foil Electrial zine board Electrial zine board 1.2TP2Y 1.2TP2Y 2.02 2.28 4.67 5.26 / /
PRODUCT SPECIFICATIONS The manufactur reserves the right to change any change any product specifications without notice. Item Cooling capacity Heating capacity Power supply Power input Cooling Running current EER Power input Heating Running current COP Indoor side Sund Leval Outdoor side Height Case Width Depth Height Packaging Width dimensions Dpth Net Weight Gross Type Model Compressor Running cap. for comp. Starting method Heating side Pressure Cooling side Model Refrigerant charge indoor unit Type outdoor unit Fan Fan speed Hi Lo Running capacitor Air direction control Air volume Monisture removal Moisture removal Attestation Compressor oil charge Exchanging pipe type/diameter Fin factor Fin material Case material Type of capillary Total area of evaporator Total area of conenser Pipe connection UNIT BTU/h BTU/h W A BTU/(hW) W A BTU/(hW) dB(A) dB(A) HAM-07C03 HM-07C03/R7000 / / 1PH,220~50Hz 1PH,220~50Hz 4.3 4.3 8.7 8.8 / / / / / / / / TOSHIBA TOSHIBA PH135X1C-4DZ2(2000165) PH135X1C-4DZ2(2000165) PSC 2.65 0.65 R22 0.52 inertial fan / 30 60~1.6 10-3 CE 400 evaporator: 7 : 9 / Hydrophile aluminum foil Electrial zine board 1.2TP2Y 1.77 4.09 / PSC 2.65 0.65 R407C 0.6 inertial fan / 30 60~1.6 10-3 CE 400 evaporator: 7 : 9 / Hydrophile aluminum foil Electrial zine board 1.2TP2Y 1.77 4.09 /
Heating Sund Leval Case
Packaging dimensions Weight Compressor Pressure Refrigerant
MPa MPa kg
r/min m3/hr m3/hr ml mm
Air direction control Air volume Monisture removal Moisture removal Attestation Compressor oil charge Exchanging pipe type/diameter Fin factor Fin material Case material Type of capillary Total area of evaporator Total area of conenser Pipe connection
r/min r/min F m3/hr m3/hr ml mm
3 PRODUCT SPECIFICATION
MAIN COMPONENTS AND ACCESSORIES'NME,DEMENTION AND FUNTION HM-07C03, HM-07C03/R1,HM-09CA03
MAIN COMPONENTS AND ACCESSORIES HM-07C03 Structural faeature cooling capacity voltage Type product Apppeatance feature attestation remote refrigerant Climate type dimensions packege dimensions Box up document No CE No R22 T499 788mm 1147 mm No CE No R407C T499 788mm 1147 mm No CE No R22 T499 788mm 1147 mm No CE No R22 Tmm( 1147 mm( ) Bacl Hot air exhaust duct )
Water tank Gaster wheel Power pulg
HM-07C03/R1 Mobile air conditioner 7000BTU/h 220V Mobile air conditioner series
HM-09CA03 Mobile air conditioner 9000BTU/h 220V Mobile air conditioner series
HSM-08C03 Mobile air conditioner 8000BTU/h 220V Mobile air conditioner series
Machine body Front
Mobile air conditioner 7000BTU/h 220V
Mobile air conditioner series
Vertical pendulum blade
Top air intake bar Water exit
Use to connect the drainage Do not pull out-this part When the drainage is not used or it may result in leakage of water
Hot air exhaust exit
Accessories of hot air exhaust duct
Low air intake bar
HSM-08C03 Control panel Water full indicator Fan selection key The running indicator of the compressor LCD
Running mode key
MODE FAN SPEED LOUVER
Sweeping key Vertical pendulum blade
Temperaure setting key
Time setting key
Gaster wheel Power plug Water tank
Sleep setting key
LCD windo Connecting pipe Displaying of Displaying of dehumidifying Cooling Displaying of sleeping Handle Fan mode Displaying of the tan speed Air outlet(outdoor) Air outlet (indoor) Air filter
FAN SPEED SET TMEP
Displaying of automatic sweeping Displaying of the set temperaaure
Displaying of timing Displaying of timing mode Foot wheel
Control panel Water full indicator Fan selection key The running indicator of the compressor
LCD windo Displaying of Displaying of dehumidifying Cooling Displaying of sleeping
Fan mode Displaying of the tan speed
Displaying of timing Displaying of timing mode
FUNCTION 1.Running Mode Key press the key to choose from three running node:cooling mode:cooling dehumidifying Fan.The LCD window displays correspondingly: 2.Fan Seletion Key Press the key to choose from three fan speed:high middle low.The LCD windo displays correspondingly: 3.Sweep key: Press the key to enable automatic side-to-side sweeping of the indoor air.The LCD window displays ;press the key again to fix the indoor air at present direction. 4.Temperarure Setting key Press the key to set the temperarure between 10-30.Each press of the part will increase the remperarure for 1 each pressg of the part will decrease the temperarure for 1.The temperature will be displayed in the LCD window. 5.Sleep Setting key Press the key to set or cancel Sleep Mode.When the LCD window displays the air conditioner is nuder Sleep Mode.Press again to cancel the Sleep Mode,and the signal will disappear on the LCD indow. 6.Power Switch key Power Switch on/off the power of the air conditioner. 7.Time Setting key: Press the key to set or cancel the Time Mode,or set rime berween1-24hours.Each press of the part will add one hour. which will be displayed on the LCD window, each pressing of the part will reduce one hour, If it shows 1 hour.Press once to cancel the timing. 8.Water Full indicator of: When the water rank is filled with water, the indicator will flash,and alarm iwth veep.The compressor stops working.The air conditioner enrers fan mode.Please take our the water tank. Pour the condensed water, then replace it. The air conditioner runs as per the mode vefore stopping of the compressor(the compressor can only start after 3 minutes of time-delay protection). 9.The run indicator of the compressor: In cooling or dehumidifying mode, the indicator will be on in the running of the compressor.
KNOCK-DOWN DRAWZIN AND ITST OF COMPONENT HM-07C03, HM-07C3/R1,HM-09CA03
Model:HM-09CA03 Special N NO. O. Name Evaporator Assembly Side plate,left Draw board Indoor intake bar Condenser assembly Support bar Compressor Nut special Cushion rubber Bottom plate Wheel Rear panel Discharge pipe Suction pipe Front plate Front panel Storage tank base board Storage tank Micro switch Strong tank cover Partition plate assy Protective plate Drain pan Cover Vendiduct(outdoor) Cover panel Outside fan Cover Vendiduct cover(outdoor) Motor(down) Compressor capacitor Capacitor clamp Side plate right Support plate Drain pan Vendiduct (indoor,down) Inside fan Vendiduct (indoor,up) Electric board Tronsormer Control board Motor(up) Fan capacitor Motor capacitor Quantity description Damageable parts(yes or no) No No No No No No Yes No No No No No No No No No No No No No No No No No No No No No No Yes No No No No No No No No No No No No No No Yes Yes Cost price
Model:HM-07C03/R1 Special N NO. O. Name Evaporator Assembly Side plate,left Draw board Indoor intake bar Condenser assembly Support bar Compressor Nut special Cushion rubber chassis Wheel Rear panel Discharge pipe Suction pipe Front plate Front panel Storage tank base board Storage tank Micro switch Strong tank cover Partition plate assy Protective plate Drain pan Cover Vendiduct(outdoor) Cover panel Outside fan Cover Vendiduct cover(outdoor) Motor(down) Compressor capacitor Capacitor clamp Side plate right Support plate Drain pan Vendiduct (indoor,down) Inside fan Vendiduct (indoor,up) Electric board Tronsormer Control board Motor(up) Fan capacitor Motor capacitor Quantity description Damageable parts(yes or no) No No No No No No Yes No No No No No No No No No No No Yes No No No No No No No No No No Yes yse No No No No No No No No No No No No No Yes Yes Cost price
HSM 08C03 Indoor unit
Special N NO. O. 1231159 1101189A Name Quantity description Damageable parts(yes or no) No No No No No No No No No No No No No Yes No No Yes Yes No No No No Yes No No Yes No No No No Yes No No No No No No No No No Yes No No No Yes No No No Yes Yes No Yes Cost price
Front panel verrical flap connection rod Horizontal flap Front panel inlay Top panel inlay Control panel Top panel Indoor intake bar filter Left side board Press key membrane Cover Upper motor electronic Capacitor clip Compressor motor Fan motor line contact bank scroll case cover (outdoor unit) Power cord clip Rear cover Power cord Connecting pipe bracker Sound absorption cushion copmpressor right side board Partition panel Water storage box Base board of Water storage box Foot whell chassis Pulling board Support bar baffle Water storage box xover Machine hanging board Full water switch Scroll cover(indoor unit) Cooled water box Fan(indoor unit) cover Upper scroll cover (indoor unit) Water meeting pipe clip transformer Water meeting pipe Control panel Water meeting tray Synchronous motor Brace of Symchronotus motor flat board of flap condenser
Outdoor unit) N O. Special NO. Name Quantity Description Damageable parts(yes or no) No No No No No No Yes No No Yes No No No No No
Inlet bars Case Handle holder Handle abutment Handle Connecting pipe group Axial fan Motor holde Outdoor fan Connecting baseboard Side board Condenser Cord board Wind circle Outdoor chassis pipe
THE FUNCTION OF ELECTRIC CONTROL CONTROL INTRODUCTION Flow chart for operation Load the subprogram of I/O sampling and process the sampling data.
Switch on power and test
Delay for 20 ms
Hsa one second passed?
Initialize the RAM I/O port and special register Load the subprogram of time handling,which requires precision within one second (Such as restarting the compressor after 3 minutes delaying etc.)
The buzzer rings twice The LCD displays the whole screen for 2 seconds
Hsa one second passed? Clear the LCD screen
Have10 ms passed? Y
The major loop
Load the subprogram of time handliing which requires precision within one minute (such as the Timing on/off, sleep,etc)
Load the subprogram of LCD display (including blade,Mode,Fand sleep,Timing and Temperature)
Is there something wrong with the temperarure sensor?
Load the subprogram of keyboard processing
Has the water been full ofr 3 minutes?
Load the subprogram of fast-test concluding Handle it as switching off power
Have 25 ms passed?
Judgement and processing of the key value
Return to the major Loop
Perform the conclusion processing to show if the water is full and if it passes for 3 minutes.
Is the conditioner open?
B:Block W:White BR:Bnown BL:Blue R:Red Y/G:Yellow/Greer OR:Orange
Synchro BR motor
Fan capocitor BR
Upper for moton
Is it under the cooling mode?
Handle it as switching off power
BR BL BR
PH4 PH3 PH2 PH5 CN4
Power otug Y/G
Trons BL CN2
PH6 R R C
LCD TH2 Piping tenp Sensor Room temp sensor
Is it under dehumidifying mode?
Waer switch R
TH1 CN5 CN6
Y/G B B Compressor capocitor
Load the subprogram of the cooling mode
Return to the major Loop Load the subprogram of ventilating mode
Fan motor capacitor BR Synchro- BR M motor BL Return to the major loop
Pomer Plug BR
W B BL OR
L N Y/G
PH4 PH3 PH2 PH5 W
3.15A 250VFuse Trans
BL PH6 R Retoy CN3
CN2 LCD TH2 CN5 Water switch TH1 CN6 Piping temp Sensor Roon temp Sensor
Outdoor fon motor
B R R R R
Fan motor capocitor
R B Y/G
R:Red W:White B:black BL:Blue BR:Brown OR:Orange Y/G:Yellow/Green
Page 2 4
9.Maintenance and trouble shooting 9.1.Maintenance manual 1) Functional instruction 1.Run mode:cooling dehumidifying air flowing 2.Fan adjusting:HI MID LO 3.Timing:Timing on 1-24 h Timing on 1-24 h 4.The set temperature range:15 -30 5.Swing automatic swing or fix at a poing 6.Sleep:8 hours 2)Instruction of the run mode: 1Cooling node: (1)The inner initialized set temperarure is 24 and the initialized fan is HI. (2)The fan speed is adjustable, in turn of HI MID LO (3)Asjusting of the temperature: Each pressing of the key will increase the set temperarute for 1 till it reaches30 , Each pressing of the key will decrease the set temperarure for1 ,till it reaches 15 (4)Adjusing of the air direction: Under the mode of inner fan running, the air direction can be adjusted by,the synchro motor to control the starting and closing of the motor 2.Dehumidifying mode: (1)The fan speed is not adjustable Incase of the ambient temperarute>15 ,the fan speed is LO.and sompressor is open; Incase of 12 ambient temperature 15 ,the fan speed is MID,the Compressor is open; (2)The air direction is adjustable. (3)The set temperarure is not adjustable. 3)Air supply mode: (1) Water full protection Under any node, when the water full protectuin is detected to be activated,the buzzer will beepseveral times consecutively,and the water full alarm lamp will flash on and off with a 0.5 second frequency.The compressor and outer fan will stoprunning.It will enter air supply mode.The inner fanwill ren at the former speed.If the water full protection is released in 3 minutes,the controller will run under previous set mode and the water full alarm lamp will be off.If it is not released in 3 minutes,. the inner fan will stop running either and whole machine is under stand-by mode,.But the water full alarm lamp will keep on flashing rill it is released. 2.Ppotection against freeaing When the coildepipe temperature sensor detects that the surface temperatrue of the avaporator T -2 ,the compressor and the fan will stop running,the inner fan will run at HI speed and the Fan key will be impotent.When the detected temperature>-8 amd the stop time of the compressor is longer than 3 minutes, the compressor and the onter fan will be started and the inner fan runs at set fan speed. 3. Prtection of the compressor The compressor must be restarted after 3 minutes from the former stop,except for the power failure. 5) Sleep prostection 1.the function is only activited under cooling mode, and impotent under other modes. 2.Afer one hour running under cooling sleep, the set temperature will rise for 1 ,and rise for another 1 after one another hour,after another6 hours of running the complete machine will be shut down. 3.In case that Sleep and Timing Off are set at the same time, the first impotent not will be activated. 4.In Sleep mode the Timing On will be impotent. 6)Timing function 1.The timing Off can be set when the machine is rumming;the Timing On can be set when the machine is shut down. 2.The timing range is 1-24h; Each pressing of the key will raise the set time for 1h;each pressing of the key will reduce the set rime for 1h.When it is added to 24h the key or key will cancel the timing.
9.2 Trouble shooting No. 1 Phenomenon The complete machine does not start without any reflection after the power is switched on Reason No power supply or abnormal power suopply The fuse is broken The corrugated copper plate is burnt The L end and compressor end of the compressor relay are mixed up The plug between the high electroplte and the weak electroplte, or between the transformer and transformer and the circuit board is loose. The indoor temperature sensor pack is with open circuit The water tank is full of the water level seitch is with short circuit The refrigerating medium is leaking. The refrigerating system is blocked. The compressor is broken down. The air circulation is bad The fan setting is not reasonable. The components are loosen. The fan is off-center. The compressor is broken down. The water level switch is with open circuit. The connector of the sweep motor is loosen. The spot weld of the sweep motor is with rosin joint. Tht swep motor is broken down. There's mechanical resistance with the sweep mechanism. The LCD foot is with rosin jiint The LCD is broken down. Remedy Check if the power line and plugs are well Replace the fuse Check out the reason of burning, and welding the copper plate after debugging Change the terminals Insert the plug firmly
10 SYSTEM FLOW CHART (1) Refrigerant using: HM-07C03 uses freon R22 as its refrigerant, when leaving factory, refrigerant charge is 0.52 g HM-07C03 R1 uses freon R407C as its refrigerant, when leaving factory, refrigerant charge is 0.52 g HM-09CA03 uses freon R22 as its refrigerant, when leaving factory, refrigerant charge is 0.6 g HSM-08C03 uses freon R22 as its refrigerant, when leaving factory, refrigerant charge is 0.75 g (2) system vacuumize: After whole set of mobile air conditioner assembling is finished,, use vacuum pump to draw out air and water in the indoor unit. System vacuum tolerance will be under 200Pa (3) Diagram of pipe system:
The LCD displays, but the complete machine can not start.
The refrigerating works with bad effect
Check the circuit of the temperature sensor pack Discharge the water or check ` the circuit of the water level switch. Detect the leakage and fill the refrigerating medium. Clean the pipeline system. and fill again. Replace the compressor. Clean the filter screen. Set reasonable fan speed.
The noise is large.
Th machine does not stop after the water is full The sweep fins do not move or move abnormally.
Find out the loosen part and fasten it Replace the fan Replace the compressor. Check and repair the water level switch circuit. Repair or replace the connector. Weld the spot to be under good condition. Replace the sweep motor. Repair or replace the sweep spindle, pitman, pins.
1. Evaporator 3. Compressor 5. Connecting pipe 7. Main capillary
2. Gas & liquid separator 4. Fast tie-in 6. Condenser
The LCD is not complete or not clear
Check the spot weld. Replace the LCD or major control board.
(4) type of compressor and compressor feature:
INSTALLATION AND REPAZRING
220V-- 50Hz-- 1PHASE SUCTION GAS TEMP.-- 35 ( C) UNDER COOL ---------- 8.3 ( K) AMBIENT TEMP. ---- -- 35 ( C) RUNNING CAPACITOR--25 MFD
In order to make the air conditioner to work effectively, first need to calculate the cooling capacity of the air conditioner, according to the room size and surroundings. After selecting a proper one and putting it in a suitable work place, place, please confirm the place to install the air conditioner referring to the following instruction: 1. Better install the outdoor unit in the outdoors to make an easy heat exchange. The ideal place: out of window, balcony, corridor and so on. To make the oudoor have an easy heat exchange, please leave the distance between the back of outdoor unit and the wall or other things no less than 5CM. (Fig.1) The specific installation process refers to installation.
FLOW RATE (kg/h)
The bracket to support the outdoor unit should be strong and firm, and endure the pressure of the unit. Regularly check the bracket about its firm condition and rusted degree to avoid accidents. Only using the connecting pipe to hang the outdoor unit is definitely forbidden. 2. The left side of indoor unit should leave the objects (such as curtain. wall, etc) no less than 20CM. To guarantee smooth ventilation the alien things should not block outlet. (Fig.2) 3. The connecting pipe can cross the chink of the window. When the unit in operation, the window should be closed as tight as possible to avoid the loss of energy. (Fig.3) 4. If you want to close the window tight, you can cut a 55 25mm2 hole in the window frame, the location of the hole can be decided according to concrete condition. After the connecting pipe crossing the window, sealing glue should be used to avoid entering of water. (Fig.4)
10 ( C)
CONDENSING TEMP. (
4.0 3.5 3.0 2.2750
5.0 4.5 4.0 3.5 3.3000
EFF AMP Pin Pout N.mm
0.8.28 7.160 0.7.14
0.6.4.5.120 0.5.10 0.4.08 6.0
0.3.0.2 0.0.1.0.0 0.6 220.127.116.11.04 0.1.02 0.0.00
1.0 1.2 KRPM
Pin AMP EFF 180.54 160.48 140.42 120.36 100.30 80.24 60.18 40.12 20.06 0.00 0.9 0.8 0.7 0.6 0.5 0.4 0.3 0.2 0.1 0.0
Pout N.mm 50 0.00.10.20.18.104.22.168 KRPM.70 Pin
8. List of main material for PCB
8. 1 Main PCB
AC-N SWING RY5 PH1 FUSE 3.15A/250V
LF MF HF CN1 RY4 RY3 RY2
R2 VAR1 C10
C5 C216W CN2 CN3 U7
U1 D4 D3 D2 D1 C1
Name Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Precision resistance Exclusion Electrolytic capacitor Electrolytic capacitor Electrolytic capacitor Electrolytic capacitor Ceramic capacitor Ceramic capacitor Diode Diode Triode Voltage-regulator diode Light-emitting diode Crystal oscillator Integrated package IC IC Inductance Buzzer Piezoresistor High-voltage capacitor Protective tube Protective tube seat Pin Needle file Needle file
Model&Spec. 47 1/4W 100 1/4W 510 1/4W 1K 1/4W 10K 1/4W 100K 1/4W 1M 1/4W 4.3K 1/4W A103 10K 5P 47 F/16V 100 F/16V 470 F/16V 1000 F/25V 104 30P IN4148 IN4001 9013EBC 3V 3 Red, green 4.19MHz 7805 uPD75P330 H HDK 500NR-10D 0.1 F250V 3.15A/250V 6.3X0.8 VH-7 XH-7
Single machine each 2 1
8. 2 PCB of panel
No. Name High-voltage capacitor Protective tube Protective tube seat Pin Needle file Needle file Needle file Needle file Needle file Needle file Needle file Press key Relay Relay LCD PCB PCB Temperature response head Temperature response head Wire bundle Jumper Jumper Model&Spec. 0.1 F250V 3.15A/250V 6.3X0.8 VH-7 XH-7 XH-3 VH-3 S-EH-2 S-EH-7 S-XH-6 5mm AJM12113 OJE-SH-112DM C216L C226W Length of the glass tube 55cm Length of the copper tube 68cm YD-7 10mm 5mm Single machine Remarks 1 Sheathing 1 Row needle sheathing, 1 heat-shrinkable tube 4 sheathing
C24 J7 J18
J1 J2 J3 J4 Y1 ZD1 R5 R6 R7 R8
J16 R19 C22
R11 R12 R13 J8 J9 J10 J11 J12 J13 C13
D1 C17 R16
L1 J20 C25
Name Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Carbon-film resistor Precision resistance Exclusion Electrolytic capacitor Electrolytic capacitor Electrolytic capacitor Electrolytic capacitor Ceramic capacitor Ceramic capacitor Diode Diode Triode Voltage-regulator diode Light-emitting diode Crystal oscillator Integrated package IC IC Inductance Buzzer Piezoresistor
Model&Spec. 100 1/4W 200 1/4W 510 1/4W 1K 1/4W 10K 1/4W 100K 1/4W 1M 1/4W 4.3K 1/4W A103 10K 5P 47 F/16V 100 F/16V 470 F/16V 1000 F/25V 104 20% 30P 20% IN4148 IN4001 9013EBC 3V 3 Red, green 4.19MHz 7805 uPD75P330 H HDK 500NR-10D 5% 5% 5% 5% 5% 5% 5% 5%
Single machine each 1
Tel :86-532-8938356 Web site : http://www.haier.com
21PT135B Abit KN9 Extender XV-EV700 2400MP System I SB-HD41R TX-DS787 DN-C635 L1953HM-SF TX-14S3TP NW-S202F Squad CDX-C7100 Ho-2005 KV-32FX20B Watch C NV-MX1 C-100 MYH10 DB346MP TU-PT600B MP0603H Speakers Micropiano DJ-175 TFH VTX-D800U Urc-6210 KX-TG2208 KX-TG7160E MS-07AH Nq0 Quilter 7350 LQ-1170 PSR-E313 XM3520 CD4402S Urc-8011 PV-GS120 DR175B EB-GD52 MF5550 Aspire 5670 Officejet 7210 NRB30FX1 67-250 Hdmi NE-691 SX-M100 Quick 3 337 407 P910I Finepix A800 BH-214 ES-2140 A Mexico W6021 LST244T-2 ER8761B AWT 2241 Audi S8 350Z-2006 CDX-2250 6432TD Rage-2006 CC-RD100 KV-25DA1 MB-3907C Minolta 7020 Heresy III WS9160 9800D LE32R86WD IC-Q7 XU-301 DCR-DVD406E I1035 ZB271RF Review Siemens S66 CE1071-S-XEN FB162-A0U Minolta 7272 RX-D10 7130S KTM 525 Hammond XM-2 Asus A3 19LS4R Witl 106 6015I 203FE M600- Digimax 3100 Canon Nokia 5230 10685 JOG-2000 DMC-LZ7 VR-5505 HDC-HS60 Tomtom XXL Izzi ALU
manuel d'instructions, Guide de l'utilisateur | Manual de instrucciones, Instrucciones de uso | Bedienungsanleitung, Bedienungsanleitung | Manual de Instruções, guia do usuário | инструкция | návod na použitie, Užívateľská príručka, návod k použití | bruksanvisningen | instrukcja, podręcznik użytkownika | kullanım kılavuzu, Kullanım | kézikönyv, használati útmutató | manuale di istruzioni, istruzioni d'uso | handleiding, gebruikershandleiding
1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24 25 26 27 28 29 30 31 32 33 34 35 36 37 38 39 40 41 42 43 44 45 46 47 48 49 50 51 52 53 54 55 56 57 58 59 60 61 62 63 64 65 66 67 68 69 70 71 72 73 74 75 76 77 78 79 80 81 82 83 84 85 86 87 88 89 90 91 92 93 94 95 96 97 98 99 100 101