Siemens Desigo Lonworks Networks
Here you can find all about Siemens Desigo Lonworks Networks like manual and other informations. For example: review.
Siemens Desigo Lonworks Networks manual (user guide) is ready to download for free.
On the bottom of page users can write a review. If you own a Siemens Desigo Lonworks Networks please write about it to help other people. [ Report abuse or wrong photo | Share your Siemens Desigo Lonworks Networks photo ]
Siemens Desigo Lonworks Networks, size: 367 KB
Siemens Desigo Lonworks Networks
User reviews and opinions
|Cannonfotter||12:37pm on Saturday, October 2nd, 2010|
|Super Noisy, Hot and Slow Horrible drive. Constantly noisy. Runs hot enough to cook an egg on. Performance is really slow and frequent access errors. Fast and Cheap Got 4 of these from Amazon at very good price. Drives are super fast, running HyperV with a bunch of VMs.|
|chiriones||11:57am on Wednesday, September 15th, 2010|
|Great fast drive, roomy enough for software developing tasks This is a great fast drive, runs circles around my old consumer level 7200 rpm HDD.|
|cert2005||10:50pm on Wednesday, July 7th, 2010|
|Im not 100% sure, but these things are dying in the field. Be very careful Knock on wood vewwy scawwy|
|andyfrazer||3:14pm on Tuesday, May 25th, 2010|
|MacBook Pro Upgrade Bought this to improve the speed and capacity of my MacBook Pro (the version just prior to the Unibody version).|
|eckobar||4:03am on Monday, March 22nd, 2010|
|I am impressed with NewEgg.com speed - ordered the drive on late Wednesday night, got it on Friday morning. Got this as a replacement for a 80 Gig 5400RPM samsung. On Vista X64 went from a 5.1 to a 5.9.|
|marimola||5:36am on Saturday, March 13th, 2010|
|Did anyone do any QA/QC testing? Well, lets see, 6 Seagate Cheetah drives in an array, one failed within 3 months of lite use during startup.|
Comments posted on www.ps2netdrivers.net are solely the views and opinions of the people posting them and do not necessarily reflect the views or opinions of us.
BACnet Router for LONWORKS Ethernet/IP
BACnet Router for LONWORKS Ethernet/IP BBMD BACnet Broadcast Management Device Communication statistics BACnet device object Connection for tool and MMI
Application The BACnet router is always used where DESIGO PX automation stations must communicate via Ethernet/IP. The automation stations are connected with each other via LONWORKS and form a segment. Local LONWORKS segments are connected via Ethernet/IP (backbone). A BACnet router is required for each LONWORKS segment.
BACnet over Ethernet/IP (backbone)
PXM20 BACnet over LON
PXG80-N BACnet over LON
PXC64-U with PXM20
Functions The BACnet router transmits the BACnet protocol from LONWORKS to Ethernet/IP. This means that the two sides form a BACnet network each. Only those packages are transmitted which must go from one BACnet network to another. Local broadcast messages are limited to the local network whereas global broadcasts are not limited. BBDM In addition, the BACnet router supports the functionality of the BBMD (BACnet Broadcast Management Device) in order to distribute the BACnet broadcast messages across the IP routers. The BACnet router contains a device object and can be operated by a BACnet client (PXM20, DESIGO TOOLSET / XWORKS plus or DESIGO INSIGHT). The current operating state, date and time as well as the statistics for the sent packages are stored in the device object. These values can be read from the device object via simple read services.
The compact construction enables the BACnet routers to be used in highly confined spaces. A BACnet router is especially suitable for compact control panels or buildings services systems with integrated control panels.
2/10 Siemens Building Technologies PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
Description Metal housing Front cover LED indicators Printed circuit board Upper terminals for power supply and RJ45 connection for Ethernet Lower terminals and RJ45 for LONWORKS connection Slider for mounting on DIN rails
3/10 Siemens Building Technologies PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
Upper LED display
00406 BACnet over Ethernet/IP STATUS SERVICE TX RX INFO
Activity Continuously off Continuously on Short period off
No supply present. Check supply. Supply ok; firmware functions ok. Restart of BACnet router. Occurs periodically BACnet router must be replaced. Everything ok. Hardware fault detected during self-test. BACnet router must be replaced. Lithium battery empty. Replace battery (see maintenance guidelines). No valid firmware present. Reload firmware. Everything ok. Network fault, no link pulse from hub. Check Ethernet link from BACnet router to hub. IP address not configured. BACnet router must be configured with DESIGO TOOLSET / XWORKS plus.
Continuously off Continuously on Flashing slowly Quick flashes
Continuously off Continuously on Flashing
TX RX INFO
Yellow Yellow Red
Flashing Flashing Continuously off Continuously on
Sends Ethernet/IP packages. Receives Ethernet/IP packages. Everything ok. Detects communication loop; correct functioning cannot be guaranteed. Check network topology and re-configure BACnet router with DESIGO TOOLSET / XWORKS plus.
Router table or device object not configured. BACnet router must be configured with DESIGO TOOLSET / XWORKS plus.
4/10 Siemens Building Technologies PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
BACnet over LonTalk SERVICE TX RX
Activity Continuously off Special flashing pattern: Continuously on
Everything ok. The BACnet router has received a wink command which can be used during commissioning for the unique identification (see commissioning instructions below). The LONWORKS connection (Neuron chip) is not ready to use. BACnet router must be configured with DESIGO TOOLSET / XWORKS plus. If the LED is still on after the re-configuration the
LONWORKS connection must be faulty.
The BACnet router must be replaced. Flashing regularly: LonTalk address not configured. BACnet router must be configured with DESIGO TOOLSET / XWORKS plus. LED short period on TX RX Yellow Yellow Flashing Flashing Restart of Neuron chip. Sends LonTalk packages. Receives LonTalk packages.
Engineering notes A static IP address, a subnet mask and a default gateway must be assigned to each BACnet router during commissioning. Normally, the network administrator is responsible for the management of these addresses. DHCP (Dynamic Host Configuration Protocol) is not supported. It must also be noted that BACnet communicates on IP via a static UDP port number. The UDP port number is determined during commissioning. When using a firewall it is necessary to enable the relevant IP address and the UDP port number. Limitations Max. ten BACnet routers can be configured as BBMDs. This means that one site cannot comprise more than ten IP subnets which are separated by IP routers. Max. ten foreign devices can be entered per BBMD. A management station in a remote IP segment is a typical foreign device. Mounting instructions The BACnet router can be snap-mounted on DIN rails or directly screwed to a mounting plate.
In order to prevent equipment damage and/or personal injuries always follow local safety regulations and the required safety standards.
5/10 Siemens Building Technologies PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
Installation It is essential to adhere to the guidelines described in the mounting and installation manual (CA1Z9251). The Ethernet connection to the next hub must, for example, not be greater than 100 m.
Commissioning notes The router is commissioned and configured on the LONWORKS side using the DESIGO TOOLSET / XWORKS plus. During the commissioning the addresses and parameters of LonTalk, UDP/IP and BACnet are added. In addition, the network numbers of the directly connected BACnet networks are parameterised and the BBMD table is loaded. For a unique identification of the BACnet router in the LONWORKS network press the service pin on the printed circuit board. Alternatively, a wink command can be sent to the BACnet router. After receiving a wink command the BACnet router responds with a special flashing pattern (lower SERVICE LED). Special flashing pattern for wink command After receiving the wink command the lower SERVICE LED flashes as follows:
21s 5 Hz 5 Hz
The SERVICE LED lights up for 2 seconds, flashes for 1 second in 5 Hz pulses, then lights up again for 2 seconds, etc. until 21 seconds have passed.
After configuration, the red LEDs must not be on or flashing.
Force Firmware Download button Service pin
When a BACnet Router is no longer required, the configuration should be deleted. This can be done in two ways: a) Delete the configuration with DESIGO TOOLSET / XWORKS plus or. b) Delete the configuration directly in the BACnet Router. Procedure: 1. Switch off the power supply to the router 2. Before switching on again, press the Force Firmware Download button, then switch on the power again, keeping the button depressed until the INFO-LED starts flashing. Result: 1. The configuration is deleted and the diagnostic data is reset. 2. Both the SERVICE-LED and the INFO-LED flash.
PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
6/10 Siemens Building Technologies
Maintenance Lithium batteries usually have a life span of at least four years. The STATUS LED flashes when the battery is low. In order to prevent the loss of statistical data or date and time always ensure that the power supply is on whilst changing the battery. To change the battery pull down the front cover.
To prevent hardware damage by electrostatic discharge (ESD), a wrist strap with earth cable must be used during the battery change.
Disposal The unit contains electric and electronic components and must not be disposed of with domestic waste. Lithium battery, printed circuit board and housing must be disposed of separately The local and actual regulations must be observed.
Operating notes A configured BACnet router supports the ICMP (Internet Control Message Protocol) ping command. Other ICMP messages and SNMP (Simple Network Management Protocol) are not supported. The network load on the LONWORKS side depends on the data exchange of the connected automation stations and operator units. The bus traffic on the IP side is generated by the management stations on Ethernet/IP or superposed data exchange (Ethernet/IP as backbone). BACnet broadcast messages generate further bus traffic. Broadcast messages are passed on to the BBMDs and foreign devices. If the Ethernet/IP network is used by other systems (e.g. data processing) these loads must be taken into account. In comparison with the bus load of the BACnet devices the bus load of data processing systems is higher by several factors.
BACnet device object properties The following properties represent the current operating state of the BACnet router. They can be read by a BACnet client via the Read Property service. Router table and device object are correctly configured. Router table or device object are not correctly configured. BACnet router must be configured with DESIGO TOOLSET / XWORKS plus.
System_Status OPERATIONAL NON_OPERATIONAL Reliability
Everything ok. The LONWORKS connection (Neuron chip) and /or the Ethernet connection (COM server) are not ready to use. BACnet router must be configured with DESIGO TOOLSET / XWORKS plus. If the status still remains on NO_OUTPUT after a renewed configuration the BACnet router must be replaced.
7/10 Siemens Building Technologies PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
Network fault is detected as no link pulse is received from the hub. Check Ethernet connection from BACnet router to hub. BBMD loop detected as more than one BBMD appears in one IP segment. Check network topology and configure BACnet with DESIGO TOOLSET / XWORKS plus. Because of a network loop, for example, the router functionality cannot work correctly. Check network topology and configure BACnet router with DESIGO TOOLSET / XWORKS plus Other faults, for example low battery (see STATUS LED).
General device data
Operating voltage Protective extra-low voltage PELV Frequency Power consumption Internal fuse Processor Memory space FLASH RAM Througout LONWORKS Ethernet/IP
AC 24 V 20 % HD 384 50/60 Hz max. 6 VA thermic, automatic reset Motorola MB 1 MB min. type max. max. typ. min.
Latency LONWORKS Ethernet/IP
30 packages/sec. 50 packages/sec. 80 packages/sec. 50 ms 30 ms 15 ms
Data backup in case of power failure Configuration parameter (FLASH) Lithium battery Power supply Plug-in screw terminal
> 10 years > 4 years typical stranded or solid conductors 0.25 to 2.5 mm2 or 2 x 1.5 mm2 TP/FT-10 FTT-10A 78 kbit/s BACnet protocol over LonTalk RJ45 socket unscreened stranded or solid conductors max. 3 m
Interface type Transceiver Bit rate Protocol Pin Plug Plug-in screw terminal Wiring, RJ45 Connecting cable PXM20/DESIGO TOOLSET / XWORKS plus Wiring, plug-in screw terminal Cable type Cable lengths
2-core, twisted pair, unscreened max. 450 m in free topology max. 900 m in serial topology
8/10 Siemens Building Technologies PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
Interface type Bit rate Protocol Pin Wiring Cable type Cable lengths Protection standard to EN 60529 Isolation protection class Operation: Class 3K5 as per IEC 721 Temperatur 0. 50 C Feuchte < 85 %rH Product safety Automatic electronic controls for household and similar use Special requirements for energy controllers Electromagnetic compatibility For residential, business, general commercial and light industrial use. Interference immunity Emitted interference Meets requirements for CE marking: Electromagnetic compatibility UL-Approbation
10BaseT, IEEE 802.3 compatible 10 Mbit/s BACnet over UDP/IP RJ45 socket screened standard CAT5 UTP1) or STP2) max. 100 m IP20B III Transport 2K3 as per IEC 721 25. 65 C < 95 %rH
Housing protection standard Protection class Ambient conditions
EN 60730-1 EN 60730-2-11
EN 61000-6-2 (Industry) EN 61000-6-3 (Residential) 2004/108/EG UL 916: PAZX, PAZX7
See "Dimensions" Including packaging
approx. 1 kg
UTP Unshielded Twisted Pair
STP Shielded Twisted Pair
AC 24 V 6 VA
LON MMI TOOL CLA 51 CLB
Terminal Name TE G|G0 Ethernet MMI/TOOL CLA|CLB
Description Functional earth Supply voltage AC 24 V Ethernet network connection RJ45 socket (for PXM20 operator unit or DESIGO TOOLSET / XWORKS plus) LONWORKS network connection
Siemens Building Technologies
PXG80-N BACnet router for LONWORKS Ethernet/IP
Sockets LONWORKS RJ45 socket unscreened, connection for DESIGO automation stations
LONWORKS, Data A (CLA) LONWORKS, Data B (CLB) G0/GND G/Plus
Unoccupied Unoccupied COM1/TxD COM1/RxD
RJ45 socket screened, standard connection acc. to AT&T256
Tx+ TxRx+ Unoccupied
5. 6. 7. 8.
Unoccupied RxUnoccupied Unoccupied
Dimensions in mm
2000 - 2009 Siemens Building Technologies Ltd.
Subject to change
10/10 Siemens Building Technologies
LONWORKS , LonTalk and Neuron are registered trademarks of Echelon Corporation PXG80-N BACnet router for LONWORKS Ethernet/IP CA1N9260en_March 2009
23PF4321-01 BMG900ESL23 DX-626 19DV555DG AZ6821 Cube Q120 LP425Z DVD-P380 ML-2525 Powershot S230 Altima 2011 W 3240 CS-ME7dkeg Suunto PM-5 8 0 ZNM11X KX-TG1100CE 2 0 RM4230 I ZWD800T West 8023 VGX-TP3z B VGN-A617B Expresso 400VTX SF-7800 ECR 5800 2900I IG-80 Of Time P4M900-m7 FE ROC 3205 Loran-C NAS 110 PSS03A Samsung 172X Psr-2700 TH-42PX45EH CS TOP HM80-155267G VFW 065 Version 4 Serie Gigaset S440 Repeater DV-SP506 SCC-C9302P GM-X564 735 S 6210701X61 1792MB GS Sierra 1994 AR 687 WD-12480T GC1720 VP-DC172W Diamond IP2000 Audioline 702 Ls-GPS HL-1870N CPC-210 DES-3010PA 13N-M100 57 12 Fb795CU XJ600N-2000 Addressfixer H 4640 GWA502 K320I Polar F4 DMC-515SC Yamaha DMP7 KDC-W4537uaug KS500 SU-7100K GZ-HD5 SC-6580 TA-AV790ESD 7945G SA-PM28 MFC-5460CN K3G21-G DWL-G810 Microtower PC DSC-W370 B Software Gzmg505US-GZ-mg505 Review HC-490 ME Finepix M603 DMC-LS3 DAV-DZ310 Casio 4765 FX-85MS 128 H NN-D998W EUF2900X 840
manuel d'instructions, Guide de l'utilisateur | Manual de instrucciones, Instrucciones de uso | Bedienungsanleitung, Bedienungsanleitung | Manual de Instruções, guia do usuário | инструкция | návod na použitie, Užívateľská príručka, návod k použití | bruksanvisningen | instrukcja, podręcznik użytkownika | kullanım kılavuzu, Kullanım | kézikönyv, használati útmutató | manuale di istruzioni, istruzioni d'uso | handleiding, gebruikershandleiding
1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24 25 26 27 28 29 30 31 32 33 34 35 36 37 38 39 40 41 42 43 44 45 46 47 48 49 50 51 52 53 54 55 56 57 58 59 60 61 62 63 64 65 66 67 68 69 70 71 72 73 74 75 76 77 78 79 80 81 82 83 84 85 86 87 88 89 90 91 92 93 94 95 96 97 98 99 100 101