Installation video for Homexpert by Honeywell Room Thermostat THR830.
http://www.ultimatehandyman.co.uk/forum1/ shows how to install a wireless room thermostat to a combination boiler. Wireless ...
Honeywell's most popular Room thermostat, 230V, range 10-30degC, 10amp Available to purchase at: ...
T6360B Room Thermostat Wiring & Operation
How do I wire a T6360B room thermostat? Wiring diagram of T6360B terminals on T6360B
NOTE: Terminal 4 is the 'make on temperature ... coding in central heating wiring so we cannot recommend a "colour-to-a-number". A room thermostat is basically a switch, making and breaking a 230V electrical signal according to room temperature ... connection is made to Terminal 2 to give accurate temperature control. (The T6360B will not work on 24V) On the T6360B range of thermostats Terminal 1 is the Live IN (LINE) and ... Terminal 3 is the Switched Live OUT (LOAD). In order to respond to temperature change accurately, the room thermostat must ... have a separate Neutral connection on Terminal 2. If replacing an existing thermostat that does not have a separate neutral wire, the T6360B cannot be used. Alternatively ...